120V Underfloor Heating Mat of UL approved E481865
Senphus offers a 10 year warranty for heating mat.
Please read the complete installation instructions carefully.
Pay attention to local circumstances, standards and regulations. The Install and Test Report be filled out by a qualified electrician.
It should be kept by the owner of the building to comply with electrical regulations and the warranty conditions.
|Item No.||Voltage(V)||Power(W)||Square meter||Size(SQ,FT)|
Installation GuideFirst , prepare the floor, the floor is clean and dry, you can install the heating mats on the floor directly; you can also install the insulation board and the aluminum foil in advance.Don't lay the insulation board and the aluminum foil under the toilet,the bathtub , the floor drain area and other bathroom furniture.Second, measure up Third, cut, turn and affix matting systemDon't lay the heating mat under the toilet,the bathtub , the floor drain area and other bathroom furniture.Just Remember Wire should be laid at a minimum of 50mm and should NEVER crossNever cut the wireDo not overlap the wireWire should be fixed with the tapes or the clipsThe heating mats should be installed on the same levelTest the resistance and the insulation with the universal meter againFourth, Installing the Thermostat and Floor ProbeAll electrical work should be completed by a qualified electricianAtop the finished heating mats are cement layer, then the tiles.
|Power supply ||100-120Vac||100-120Vac|
|Power output ||100W/M2||160W/M2|
|Min. bending radius||30mm||30mm|
|Min. cable spacing ||11cm||9cm|
|Max. exposure temp. ||90oC||90oC|
|Min. installation temp. ||+5oC||+5oC|
|Cold lead cable ||3x1.0mm2||3x1.0mm2|
|Length of cold lead||2.0m||2.0m|