UL approved Heating Mats of 120V
Senphus Underfloor Heating Mats are the easiest and fastest to install, and are best suited for rectangular-shaped areas. The cable is pre-spaced on the mesh at 9cm, offering optimal heat distribution.Heating Mats of 120V Specification
| || || || || || || |
|SHHM-150-0.5M2||120||75||192.00||5.55||0.5||3C 0.75mm2 L=2M black|
|SHHM-150-1.0M2||120||150||96.00||11.1||1||3C 0.75mm2 L=2M black|
|SHHM-150-1.5M2||120||225||64.00||16.65||1.5||3C 0.75mm2 L=2M black|
|SHHM-150-2.0M2||120||300||48.00||22.2||2||3C 0.75mm2 L=2M black|
|SHHM-150-2.5M2||120||375||38.40||27.75||2.5||3C 0.75mm2 L=2M black|
|SHHM-150-3.0M2||120||450||32.00||33.3||3||3C 0.75mm2 L=2M black|
|SHHM-150-3.5M2||120||525||27.43||38.85||3.5||3C 0.75mm2 L=2M black|
|SHHM-150-4.0M2||120||600||24.00||44.4||4||3C 0.75mm2 L=2M black|
|SHHM-150-4.5M2||120||675||21.33||49.95||4.5||3C 0.75mm2 L=2M black|
|SHHM-150-5.0M2||120||750||19.20||55.5||5||3C 0.75mm2 L=2M black|
|SHHM-150-6.0M2||120||900||16.00||66.6||6||3C 0.75mm2 L=2M black|
|SHHM-150-7.0M2||120||1050||13.71||77.7||7||3C 0.75mm2 L=2M black|
|SHHM-150-8.0M2||120||1200||12.00||88.8||8||3C 0.75mm2 L=2M black|
|SHHM-150-9.0M2||120||1350||10.67||99.9||9||3C 0.75mm2 L=2M black|
|SHHM-150-10.0M2||120||1500||9.60||111||10||3C 1.0mm2 L=2M black|
|SHHM-150-12.0M2||120||1800||8.00||133.2||12||3C 1.0mm2 L=2M black|
|SHHM-150-15.0M2||120||2250||6.40||166.5||15||3C 1.0mm2 L=2M black|
Heating Mats Installation Guide
1.The insulation board must be installed if you have a wooden substrate. It is also recommended with concrete substrates to optimise efficiency and reduce warming times(up to 50% more thermally efficient).
2.Always round down your floor space area e.g. 2.6m2 of floor will require 2 m2 of matting (To avoid surplus matting).
3.Neververlap the mat, always ensure a min.50mm spacing between the wires for optimum heat distribution.
4.If there is a matting shortfall in your floor space then concentrate the heat mat in heavily trafficked areas.
5.A Residual Current Device(RCD) should be used with this system(must be bought separately).
6.Floor must be clean and free from dust & dirt.
7.Never cut the heating(red or blue color) wire or join two or more mats together in series, use a junction box.
8.Only use scissors when cutting the mesh.
9.The wire is tough but extra care must be taken when using sharp objects near the mat. a plastic trowel is advisable.
10.Check your system with a multi-meter before tile installation.
11.Ensure your tile adhesive is suitable for use with undertile heating e.g. highly polymer modified(flexible).
12.Your substrate and floor covering, e.g. tile adhesive or screed, must be completely dry before switching on your system for the first time.
13.Wear gloves when handling the mat(to avoid irritation to skin).
14.Take care when tiling to ensure your do not dislodge or damage the wire from the mesh mat.
15.The insulation board is not suitable for floor strengthening and structural reinforcing.
16.Matting and insulation board should not be passed under permanent fixings e.g. bath, toilet, etc.
17.Do not store objects on top of the matting during installation e.g. tiles.