120V Underfloor Heating Mat of UL Approved
|FOB Price:||US $8 / Piece|
|Min. Order:||1 Piece|
|Min. Order||FOB Price|
|1 Piece||US $8/ Piece|
|Payment Terms:||L/C, T/T, Western Union, Paypal, Money Gram|
- Model NO.: SHHM-150
- Power: 100W/M2, 150W/M2, 160W/M2, 200W/M2
- Type: Room Heater/ Floor Heater
- Heat Source: Heat & Power Plant
- Trademark: SENPHUS
- Specification: 0.5~12m2
- HS Code: 85168000
- Thickness: 1.5mm
- System Structure: Heating Mat
- Heat Medium: Heating Wire
- Material: CuNi
- Transport Package: Color Carton and Pallet
- Origin: China
Senphus offers a 10 year warranty for heating mat.
Please read the complete installation instructions carefully.
Pay attention to local circumstances, standards and regulations. The Install and Test Report be filled out by a qualified electrician.
It should be kept by the owner of the building to comply with electrical regulations and the warranty conditions.
|Type||Voltage||Rated power||Resistance @20oC+10/-5%||Mat size||CableLength|
|Min. bending radius||30mm||30mm|
|Min. cable spacing||11cm||9cm|
|Max. exposure temp.||90oC||90oC|
|Min. installation temp.||+5oC||+5oC|
|Cold lead cable||3x1.0mm2||3x1.0mm2|
|Length of cold lead||2.0m||2.0m|
First , prepare the floor, the floor is clean and dry, you can install the heating mats on the floor directly; you can also install the insulation board and the aluminum foil in advance.
Don't lay the insulation board and the aluminum foil under the toilet,the bathtub , the floor drain area and other bathroom furniture.
Second, measure up
Third, cut, turn and affix matting system
Don't lay the heating mat under the toilet,the bathtub , the floor drain area and other bathroom furniture.
Wire should be laid at a minimum of 50mm and should NEVER cross
Never cut the wire
Do not overlap the wire
Wire should be fixed with the tapes or the clips
The heating mats should be installed on the same level
Test the resistance and the insulation with the universal meter again
Fourth, Installing the Thermostat and Floor Probe
All electrical work should be completed by a qualified electrician
Atop the finished heating mats are cement layer, then the tiles.